Chiller for natural refrigerants ammonia (NH3, R717)
The container consists of two 20ft containers which were delivered separately.
These two containers are assembled on site and the refrigeration system is wired with the cabinet.
1. Container (container cabinet)
The entire cabinet is installed in a container and thereby it may be used where it is needed. The cabinet is installed in the container and the wiring is routed via cable lines in the ceiling area. It also has an air inlet equipped with a muffler.
2. Containers (machine unit container)
Two refrigeration systems are built in this container with each 168 kW cooling capacity. For each refrigeration system a liquid receiver, with capacity of 125 liters per system, is installed. The container has hot air suction which is equipped with a muffler. The muffler is mounted on the outer wall of the container.
-Cooling capacity Qo: 168,40 kW
-Evaporating temperature to : -7 °C
-Condensing temperature tc: + 46 °C
-Compressor type: open screw compressor